# Buffer Tank Sizing

We are showing how to size a buffer tank when you have an on/off or modulating boiler. When sizing the buffer tank, it should be sized for the smallest zone and a pre-determined run time. The runtime is your choice, usually between 10 and 20 minutes.

Buffer tanks reduce short cycling of the boiler. Most boilers are normally 100% or more oversized for the heating system. If the boiler is properly sized short cycling will automatically be reduced. When a high efficiency boiler is used the higher the turndown the less chance of a need for a buffer tank.

# Let's look at sizing a buffer tank for an on/off boiler

**V = t(Q _{hs} - Q_{loadmin})/(500 * delta-T)**

** Where:**

**V** =Minimum buffer tank volume (gallons)

** t** = Minimum heat source on time in minutes

**Q _{hs}** = Rated heat output of heat source (Btuh)

**Q _{loadmin}**= Minimum concurrent heating load when heat source is in demand Btuh

** Delta-T **= Change in average tank temperature during minimum heat source on time (f)

**Let's assume the following:**

**t **= 10-minute recovery time

**Q _{hs}** = Boiler output 68,000

**Q _{loadmin}** = Zone output 5000 Bth/h

**Delta-T** = 20f

**V** = 10(68,000 - 5000) / (500 * 20f)

**V** = 63 gallon tank

# Sizing a buffer tank for 80,000 Btu 10:1 high efficiency boiler

When calculating minimum input of a high efficiency boiler divide the input by ther turndown. Example of above boiler,

Boiler input/turndown = minimum input

80,000/10 = 8000 minimum input

**V = t(Q _{hsmin} - Q_{loadmin})/(500 * delta-T)**

** Where:**

**V** = Minimum buffer tank volume (gallons)

** t** = Minimum heat source on time in minutes

**Q _{hsmin}** = Minimum stable heat output of heat source Btuh

**Q _{loadmin}**= Minimum concurrent heating load when heat source is in demand Btuh

** Delta-T **= Change in average tank temperature during minimum heat source on time (f)

**Note:**The smallest zone must be less than the minimum output of the boiler or no buffer tank is required.

**Let's assume the following:**

**t **= 10-minute recovery time

**Q _{hsmin}** = Boiler output 8,000

**Q _{loadmin}** = Zone output 2000 BTh/h

**Delta-T** = 20f

**V** = 10(8,000 - 2000) / (500 * 20f)

**V** = 6 gallon tank

Although this will run longer cycles, I am not happy with a high efficiency boiler running a minimum of 10 minutes. I would choose 15 - 20 minutes run times.

The difference if all were the same except a 20-minute run time. would be as follows.

**V** = 20(8,000 - 2000) / (500 * 20f)

**V** = 12 gallon gallon tank

You can see to get a better run time would not be a drastic tank size change. You can see a delta-T change will change the tank size and run time.

# What if our boiler of choice is an 80,000 BTU output 5:1 turndown boiler.

Let's apply this.

**V** = 10(18,000 - 2000) / (500 * 20f)

**V** = 16 gallon tank

**But, a 20-minute runtime would change the tank size to:**

**V** = 20(18,000 - 2000) / (500 * 20f)

**V** = 32 gallon tank

# We'll add one more idea. Let's change the Delta-T to 30f

**V** = 20(18,000 - 2000) / (500 * 30f)

**V** = 21.3 gallon tank

Changing run times or tank delta-T's will change the tank size. You can play with the numbers to see what fits your application best.

** Download Excel Buffer Tank Sizing Worksheet**

After downloading open the form and enter the appropriate information in the green boxes on the worksheet.

**Disclaimer:**The information found on this website is for informational purposes only. All preventive maintenance, service, installations should be reviewed on a per job situation. Any work performed on your heating system should be performed by qualified and experienced personnel only. Comfort-Calc or its personnel accepts no responsibility for improper information, application, damage to property or bodily injury from applied information found on this website.